Page last updated Feb 17, 2016 @ 12:34am

**Voltage Drop Calculator**

Thanks
for visiting NoOutage.com to use our free voltage drop calculator.While you are here please view our specials on all kinds of backup power related products such as... * manual transfer switches * automatic standby generators * automatic transfer switches * metering & instrumentation * UPS systems Tired of paying those rising electricity rates? We also sell alternative energy products including... * micro hydroelectric systems * wind power systems * solar Are YOU ready for the next
power outage? |
Use this calculator to estimate cable voltage drop for sizing conductors. The calculation assumes uncoated copper or aluminum conductors operating at the temperature selected and is based on the ac/dc resistance or impedance from NEC 2005 Tables 8 and 9 for stranded conductors operating on a DC or AC 60Hz system. The ampacity of each conductor size in the dropdown menu below is based on NEC 2005 Table 310.16 for 60C insulated conductors rated 0 through 2000 volts with not more than three current carrying conductors in raceway, cable or earth with an ambient of 30C (86F). Note that the actual ampacity and voltage drop for your application may differ from these results but in most cases will be very close to those shown here. Units herein are American Wire Gauge (AWG) and English (feet). Note, to run this calculator JavaScripts must be enabled on your browser. Click here for alternate calculator that also includes a transformer and motor load. NOTES: -
Examples for parallel runs: 120/240V single phase system with single black-red-white conductors (installed in single conduit) select "single set of conductors", 120/208V 3phase system with 2 conductors per phase and neutral (installed in 2 parallel conduits) select "2 conductors per phase in parallel", dc system with 3 positive and 3 negative conductors select "3 conductors per phase in parallel". -
Voltage drop for ac systems should total no more than 5% under full load conditions. This is consistent with the NEC which allows a total of 5% drop for feeders plus branch circuits. Drop may be significantly larger during surge or motor starting conditions -- sometimes in the 15% to 25% range if other devices on the system can withstand this momentary dip. Voltage drop for dc systems should be designed as low as possible or less than 2%. -
For most 120/240V systems using cables of adequate ampacity, voltage drop is not a concern unless cable lengths are well over a hundred feet. A common rule of thumb is to check the voltage drop when the one-way circuit length in feet exceeds the system voltage number. Therefore, using this rule one would check the drop for a 240V system if the circuit length exceeds 240 feet.
More information about voltage drop based on IEC standards is available in the Schneider Electric Electrical Installation Guide. UPDATE: On 11/4/2009 the 3-phase %
calculation was adjusted by a factor of 1.732 |

*Are YOU ready for the next power outage?*

**
We welcome your feedback or questions. Click here to contact us.
See our Terms & Conditions before using information or
ordering from this web site.
Copyright © 1999-2016 NoOutage.com LLC. All rights reserved.**